CWL-DV Boilers using the Beckett AFII
Late last year we received
reports of poor performance in the CWL-DV using the AFII 150 burner. We contacted R. W.
Beckett and they did a re-application of this combination. If you have a customer that
reports poor combustion such as pulsation, flutter, etc., please substitute the nozzle
installed with the following Hago nozzles and settings.
.75 - 60°B Hago
.85 - 60°B Hago
1.0 - 60°B Hago
This notice is only for the Beckett AFII 150 burner on the
CWL-DV boiler only.
If there are any further question, please call for technical service at